Chipboard with integrated underfloor heating
The new profi-chip heating board features the ability to cut the board in 4 places, giving matching connections to other panels. This allows panels to be cut and for the cut ends to start the next row (min 600mm)
Panels are the standard chipboard size of 2400mm x 600mm. Profi-chip uses 12mm Pex pipe.
Installing this system:
Panels are installed onto floor joists or battens, and the tongue and grooved edges are glued to the adjoining panels, as well as to the joists. Panels are also screwed into the joists. 12mm Frankische pipe is then fitted, following the pipe layout drawing supplied with the system.
6mm plywood is bonded to the top surface after pipe installation, forming a ridged structural floor.
Floor coverings are installed directly on top of the 6mm ply.
Click to download the pdf datasheet
Suitable Floor coverings:
Tile (over 18 or 22mm plywood fitted directly to the joists
Carpets with 1.5 tog or lower
Structural timber (18-25mm)
This system can be designed with the following average pipe spacing's.
150mm (for 300mm joist spacings)
200mm (for 400mm joist spacings)
300mm (for 600mm joist spacings)
Heat pumps with 60°C water available - supplied with a pre-assembled heat-pump manifold.
Boilers with over 60°C supply - supplied with a pre-assembled boiler manifold which has a mixing unit to reduce the water temperature
This system includes the following items:
Underfloor heating manifold - pre-assembled
galvanised pipe clips - 450mm
Aluminium sheet to cover the heating area
Thermostats for each room
System control box
CAD pipework drawing
Electrical wiring guide - first fix
Electrical wiring guide - second fix
Telephone and email support